Analysis and Improvement of the Plant Health Index Used by Eskom to Assess the Condition of the Power Transformers in its Distribution Fleet.
AbstractsThere are 4359 transformers installed on Eskom's (Africa's largest utility) distribution network. The transformers range from 1MVA to 160MVA units within a voltage range of 2.2kV to 132kV. An ideal transformer health assessment is based on four parameters being the paper life, dissolved gas analysis, condition of the auxiliary components and electrical diagnostic tests. At present there is limited availability to assess the last two parameters, and DP data is also inconsistent. As a result each Distribution Operating Unit employs the use of the Plant Health Index (PHI) as an indicator of the condition of the transformers on their network. The Plant Health Index uses oil sampling data such as dissolved gas analysis, moisture in oil, electric strength and degree of polymerisation to rank the transformers into four categories, namely: low risk, low to medium risk, medium risk and high risk. The index makes use of the data most readily available to the operating units and the accuracy of the ranking system is dependent on the quality of the transformer information captured. This paper is an analysis of the current PHI, and provides insight into its drawbacks and plots a path forward for the utility with the goal of identifying unhealthy plant early enough to address the problem and prevent in service failures.
File Size: 211,3 KB
may download free of charge all publications including most recent ones
may download free of charge publications over three years old and purchase all publications
Guidelines for the use of statistics and statistical tools on life data
Guidelines for altitude correction of pollution performance of insulators
Evaluation of lightning shielding analysis methods for EHV and UHV DC and AC transmission lines
Application of phasor measurement units for monitoring power system dynamic performance
Challenges in the control center (EMS) due to distributed generation and renewables
Voltage Source Converter (VSC) HVDC for Power Transmission - Economic Aspects and Comparison with other AC and DC Technologies
Update of Service Experience of HV Underground and Submarine Cable Systems
Recommendations for testing of long AC submarine cables with extruded insulation for system voltage above 30 (36) to 500 (550) kV (This TB replaces electra article ELT_189_1)
Integration of large Scale Wind Generation using HVDC and Power Electronics
For any questions in connection with the on-line library, contact:
Publications and Editions Manager