Commissioning of VSC HVDC systems
Voltage Source Converter (VSC) technology has emerged as a commercially viable alternative to Line Commutated Converter (LCC) technology for certain applications of HVDC power transmission. With the first commercial VSC projects commissioned in the late 1990s, at the time of the development of this Technical Brochure there is over fifteen years of project and operational experience with this technology. VSC has become the preferred, if not the only, choice of technology for specific applications, including low power transfer applications, the connection of weak networks, offshore wind farm connections and d.c. grid developments.
Commissioning occurs during the latter stages of an HVDC project. It allows the HVDC supplier to verify and demonstrate the suitability of the installed equipment, the functional completeness of the system and compliance with the requirements of the relevant contracts and specifications. Commissioning also allows adjustments and optimisation to the HVDC system to be made and allows the owners, developers and/or end-user of the HVDC system to witness and be satisfied that the project and operational requirements have been demonstrated.
The Technical Brochure provides a practical guideline for the testing and commissioning of VSC HVDC schemes including a complete description of each of the three stages of commissioning (factory tests, subsystems tests and system tests). This technical brochure provides a summary of typical tests that make up each stage of testing and commissioning and for the system testing elements, provides a guide on the purpose, preconditions, procedure and acceptance criteria applicable to each test. The technical brochure also deals with other key aspects of the testing and commissioning of VSC systems, including the management of the commissioning process, training opportunities, documentation and approaches to deal with practical limitations to on site testing.
File Size: 3,3 MB
Pages NB: 5
Study Committee : B4 ?
WG (TF): WG B4.63
You might also like
may download free of charge all publications including most recent ones
may download free of charge publications over three years old and purchase all publications
Challenges in the control center (EMS) due to distributed generation and renewables
Control methodologies for direct voltage and power flow in a meshed HVDC Grid
Framework for EPU operators to manage the response to a cyber-initiated threat to their critical infrastructure
MO surge arresters - Metal oxide resistors and surge arresters for emerging system conditions
Voltage Source Converter (VSC) HVDC for Power Transmission - Economic Aspects and Comparison with other AC and DC Technologies
Update of Service Experience of HV Underground and Submarine Cable Systems
Recommendations for testing of long AC submarine cables with extruded insulation for system voltage above 30 (36) to 500 (550) kV (This TB replaces electra article ELT_189_1)
Integration of large Scale Wind Generation using HVDC and Power Electronics
For any questions in connection with the on-line library, contact:
Publications and Editions Manager