Working Group Reports
Bearing segments with plastic lining: operating and maintenance experience
Bearing segments with plastic lining instead of the traditional babbitt lining has been used for decades in hydro generator bearings. Plastic lined bearing segments are said to have a number of advantages compared to segments with babbitt lining. These advantages are often discussed and sometimes disagreed by some users.
The purpose of this study is to get the operating and maintenance experience when having generator bearing segments with plastic lining.
The study used the survey methodology whereby members of Study Committee A1 and Working Group A1.21 were asked to obtain responses from hydro power plants owners and hydro generator suppliers in their own countries. A questionnaire containing questions about bearing type, type of plastic lining, if high pressure oil lubrication is used at start/stop sequences, control marks for wear degree, purpose of using plastic lining instead of babbitt, operation experience, possibility to turn the unit by manpower after certain time of standstill was distributed to users.
The survey was limited to hydro generators with ratings greater than 10 MVA, vertical as well as horizontal units. For
vertical units it comprised guide bearings and thrust bearings, for horizontal units it comprised radial and axial bearings.
File Size: 130,6 KB
Pages NB: 6
may download free of charge all publications including most recent ones
may download free of charge publications over three years old and purchase all publications
Evaluation of lightning shielding analysis methods for EHV and UHV DC and AC transmission lines
Application of phasor measurement units for monitoring power system dynamic performance
Voltage Source Converter (VSC) HVDC for Power Transmission - Economic Aspects and Comparison with other AC and DC Technologies
Update of Service Experience of HV Underground and Submarine Cable Systems
Recommendations for testing of long AC submarine cables with extruded insulation for system voltage above 30 (36) to 500 (550) kV (This TB replaces electra article ELT_189_1)
Integration of large Scale Wind Generation using HVDC and Power Electronics
For any questions in connection with the on-line library, contact:
Publications and Editions Manager