Insulation degradation under fast, repetitive voltage pulses
The use of power electronics in industrial drives has brought several advantages (e.g. flexibility of electrical energy conversion including regenerative bracking, more compact and lightweight drives). However, power converters have been associated, already at the end of the eighties of the last century, with the reduced reliability of several components (the stators of low voltage random wound motors have experienced the most dramatic loss of reliability). In the future, these effects will become more and more an issue in the future due to the ubiquitous use of power converters in smart grids.
This brochure is aimed at presenting, for a number of equipment typologies, the reasons behind accelerated degradation of insulation systems subjected to repetitive surges induced by power electronic converters. Also, the solutions provided by the International Electrotechnical Commission for induction motors will be discussed, as they might be used as a reference for other type of electrical components. Eventually, the use of nanodielectrics as a tool to alleviate the aforementioned problems will be shortly discussed.
File Size: 3,5 MB
Pages NB: 53
You might also like
may download free of charge all publications including most recent ones
may download free of charge publications over three years old and purchase all publications
HOW TO ACCESS TO E-CIGRE?
Click here to read a short guide to setting up your account and obtaining access to the global e-cigre.org website for all technical literature.
Advanced utility data management and analytics for improved operation situational awareness of EPU operations
Technological feasibility studies for Super and Ultra Premium Efficient motors
Voltage Source Converter (VSC) HVDC for Power Transmission - Economic Aspects and Comparison with other AC and DC Technologies
Update of Service Experience of HV Underground and Submarine Cable Systems
Recommendations for testing of long AC submarine cables with extruded insulation for system voltage above 30 (36) to 500 (550) kV (This TB replaces electra article ELT_189_1)